Installing Your American-Lights™ High
Output In-duct UV Air Cleaner Is A Simple Process That Can Be
Performed By Most People.
Click Here to print a full
pdf version of our installation instructions
Please observe all warnings.
Disconnect the power source before removal or lamp replacement. The
installation procedures should have the UV lamp at a right angle to
the air flow with the UV lamp centered in the duct or plenum. Your
American-Lights In-duct UV Air Cleaner may be installed in
either the supply or return sides (coil or return as needed) or your
HVAC system. The benefits from your UV air purifier will be
equally effective no matter which side the installation occurs. Note, however, if UV lamp is installed close to
register or grill, the ultraviolet light may cause night glow effect
which may be objectionable to homeowner.
SAFETY NOTICE: DO NOT LOOK DIRECTLY INTO THE UV LAMP.
Procedure Of The American-Lights In-duct UV Air Cleaner:
established a convenient location for the UV Air Cleaner, drill one
1.3/8” hole for the UV lamp and lock nut on coupling after
placing unit in desired location. Using cotton gloves to avoid oils
on UV lamp, slide it through coupling and secure by tightening
adjustable coupling to base. Avoid over tightening to prevent
Plug socket to lamp.
Snap air cleaner's cover in place and power air cleaner to grounded
adjacent location within 6” of unit, drill a ¼" hole and
insert the glow indicator.
UV lamp replacement:
requires one HO-14 or HO-22 germicidal UV lamp, obtained from your
High Output UV Air Cleaner is the strongest, fully certified UV
air cleaner available on the air-quality market. It requires a
minimum of rules for a productive installation:
direct exposure (within 24-30”) of non-UV inhibited plastics.
(Including drip pans, plastic filter frames, etc.)
Avoid ANY location
that would permit the homeowner access to the lamp. (Example:
closet door with louvers and the unit exposed when door is open or
light is seen through the louvers.) The night light issue should
be considered if this is being placed in less than optimum
location: across top of coil @ right angles to “A”; also
Return plenum if not within visible range of filters etc. (You do
not want this where a homeowner can remove the filter and see or
touch the lamp).
While not commonly
advertised this High Output lamp will provide strong germicidal
protection for 3 years the reason - it does not cycle on/off
thereby maximizing its life and efficiency. However, to keep the
UV air cleaner in top performance range, it is recommended the UV
lamp to be replaced every year.
Review of the
specification sheet and installation instructions will provide
answers to most situations and questions.
UV lamp once per year.
We only carry one brand of
UV in-duct air purification systems -
American-Lights™ - because we know that
we're offering you the very best with these top-quality units.
American-Lights™ Air Purifiers feature:
Money back guarantee
No filters to clean or replace
- American-Lights™ In-duct Home UV Air Cleaner technology
oxidizes particulates rather than just filtering them
Custom models available for home and commercial use
Unlimited free customer support
In-Duct Page | FAQ
| Installation | How
complete line of UV commercial air
cleaners, whole house air cleaning
systems ,or UV
If you have
any questions, call us, we'll be glad to help!
Return Policy |
Us | About Us | View
Cart | Check
©2001 - 2006 - BPA Air Quality Solutions
(DBA BreathePureAir.com) is for educational and research intentions only and
is not intended as an alternative for medical treatment or advice. Use of
this website, the 90 day return policy, and free shipping is subject to our
terms of service,
and return policy.